These Records are Actual Wells tested in West Texas, one of the most hostile environments in state. Where temperatures may run from -11o F in the winter to as much as 120oF in the summer.
Case Study A1. 50HP / 38Kw Rod Pumping unit, without our technology took a 75Kw Generator to start up and run. With our 3P3 with X-Drive® technology attached, the unit was able to startup and run on a 25Kw Generator. The Power Factor was corrected from 0.45 to 0.99-1.0 with the overall power savings of over 55%, with a production increase of between 20-30%. As verified by EKM’s power metering system, and customer electric bills.
Case Study A2. A 75HP / 56Kw Rod Pumping unit With our 3P3 and X-Drive® technology attached. The unit ran continuously on solar for over 10 hours. The energy saving results were not calculated due to changes in the well, because of management changes, and other conditions beyond our control. However, the solar drive unit was designed to run 8 hours per 24 hour period. Power Metered by Fluke & EKM.
Case Study A3. A 45HP / 33.5Kw Rod Pumping unit, the power grid on that system showed the unit used 480VAC while using 40 amps or 19.2Kw, with our 3P3 with X-Drive® technology. it reduced the usage to 17 amps, for a power reduction former 33.2Kw to 14.1Kw or a 57.53% savings the electric bill . No production records were given. Power metered by EKM
Case Study A4. ESP 350HP / 260Kw Down-Hole Pump, 480VAC using 410 amps, with our 3P3 with X-Drive® technology attached the amperage was reduced to 270-290 amps, Wattage reduced from 340.4Kw down to 240.8Kw overall reduction in their Power Bill of 27.5% . No Production report was given. Metered by EKM
Case Study A5. ESP 100HP / 75Kw Down-Hole Pump, 480VAC using 112 amps, with our 3P3 with X-Drive® technology attached the amperage was reduced to 88.3 amps, Wattage reduced from 86,918.07Kw down to 65,560.00Kw overall reduction in their Power Consumption of 24.68% . No Production report was given. Metered by EKM
Case Study A6. 45HP / 33.5Kw Rod Pumping unit, Grid showed high of 45 amps low of 22 amps, with 3P3 with X-Drive® technology attached amperage was reduced to 32 high and 0.4 low amps, Power factor increase from 0.45 to 0.98 – 1.0, reduction of power 42.9% total power reduction and usage currently undetermined waiting for latest, customers utility bill, to complete verification.
Case Study B1 Shop Compressor Grid Shows 46 amps @ 480V Reduced to 26 at 480V or a 43% Power reduction.
Case Study B2 Water well Generator showing 25% reduction with 3P3 unit, customer opted to increase production, rather than taking the energy savings.
Case Study B3 150Kw Generator power reduction to Startup and RUN a 45HP Rod Pumping unit, down to a 25 Kw Generator to Startup and RUN that same unit.
Case Study B4 350Kw Generator to start-up and run a 100 HP Pumpjack, Reduced to a 150 kW Generator with the 3P3 w/ X-Drive® Technology for both startup and run. Reduce Rent Fee 30% less and Reduced Fuel 70% less to Customer